- Certification Review
Certified Control System Technicians (CCSTs) calibrate, document, troubleshoot, and repair/replace instrumentation for systems that measure and control level, temperature, pressure, flow, and other process variables.
All of the following instrumentation bus networks can be implemented with a single pair of wires, except for?
A. Foundation Fieldbus
The correct answer is B, "DeviceNet." Foundation Fieldbus (FFB), Actuator-Sensor Interface (AS-i), and Highway-Addressable Remote Transducer (HART) instrument bus networks all operate over a single pair of wires. The power for the transmitter and the communication signal are both carried over that single pair of wires.
DeviceNet requires a separate pair of wires for power and signal, with an additional shield/ground wire. DeviceNet, then, typically requires five conductors (two pairs and a shield/ground).
Reference: Goettsche, L.D. (Editor), Maintenance of Instruments and Systems, Second Edition, ISA, 2005.
We want to hear from you! Please send us your comments and questions about this topic to InTechmagazine@isa.org.