Circuit breaker-type switches
Mar 09, 2012
Circuit breaker-type switchesMedium-Voltage (5-15kV) Circuit Breaker-Type Switches transfer electrical loads between normal and emergency power sources through the carefully controlled opening and closing of circuit breakers. Medium-Voltage Circuit Breaker ATSs may be configured for open- or closed-transition transfer. All switch functions are controlled by the companyís RPTCS programmable microprocessor-based control system. Though designed for unattended operation, these switches include controls for manual operation and provide maximum protection for personnel. UL tested, listed, and labeled under UL 1008A, the switches are approved for use in legally required emergency power systems. They also meet or exceed stringent IEEE, NEMA, and ANSI standards. For either the open- or closed-transition configuration, if the primary source is lost, the control initiates an open-transition transfer to the emergency source by tripping the primary source breaker and closing the emergency source breaker. When open-transition retransfer is selected, the switch first verifies that the primary source has returned, opens the emergency source breaker, and then closes the primary source breaker. When closed-transition retransfer is selected, the switch first performs a synch check to ensure that the primary source is in synchronism with the emergency source, then parallels the two sources by closing the primary source breaker, and finally opens the emergency source breaker.
ISA Partner Spotlight
All contents copyright of ISA © 1995-2012 All rights reserved.